Located in the heart of Beverly Hills, The Wallis Annenberg Center for the Performing Arts officially opened its doors to the public in October 2013. Automated Gate Services had the pleasure of automating a customized arched vehicle slide gate for the new contemporary state-of-the-art GoldsmithTheater. The gate curvature required a customized endless idler system to accommodate the uniqueness of this elegant project.
Project: The Wallis Anneberg Center for the Performing Arts
Location: Beverly Hills, Ca
Customer: Wolverine Fence Company
Project status: Complete
Scope of work: (1) CSL24V slide gate operator, vehicle safety loops, radio controls and customized endless idlers to allow chain to swivel for curvature of vehicle gate.
When an automated vehicular gate system is installed on a property in general access applications, there must be a method to allow emergency vehicles (fire, police, ambulance) access to the property without the gate hindering their entry. The access system must allow for entry through the vehicular gate under three different and unique situations:
- The system is in service and under normal operation.
- A power failure has occurred and battery powered convenience open systems are employed.
- A power failure has occurred and the convenience open system has failed (dead or low charged battery).
Situation 1 – Normal Operation
Under normal operation, there are many devices that can be integrated with the vehicular gate system to allow emergency vehicles access to the property. When any of these devices are activated, the vehicular gate(s) is commanded to open and remains open until the device is deactivated. Typically, the emergency vehicle access device will by-pass the primary access control device (telephone entry system for example) and is wired directly to the gate operator open input. Some of these devices are listed below.
- Click-2-Enter. This system consist of a special radio receiver that allows Fire Departments, Police Departments and Ambulance companies to open the access gates by using their two-way radio installed in their trucks / cars.
- Special Keys and Key Switches – With this system, emergency vehicles each have a special access key that that activates an emergency override key switch. These key switches are typically labeled FIRE DEPT. and are installed in a location at the gate that is visible and easily accessible.
- Lock Boxes – Lock boxes are essentially the same as the key switch option in that a special padlock (that only emergency vehicles have a key too) is placed on the lock box to lock it shut. When the padlock is removed (or cut off), the lock box automatically commands the gate to open and will hold the gate open until the lock box is re-closed and locked. Lock boxes are typically labeled FIRE DEPT. and are installed in a location that is easily visible and easily accessible.
- Siren Sensors – These devices detect the “yelp” mode from an emergency vehicles siren. When the yelp is detected, the gate will open.
- Strobe Light Sensors – These devices respond to the flashing strobe light from the emergency vehicle. When the strobe light is sensed, the gate will open.
- Wireless Transmitters – Like garage door openers, wireless transmitters open the gate from a distance of 75 to 100 feet. These transmitters are specially encoded with a code that is unique to emergency vehicles.
Because of the many different devices available, the city building department should be consulted to determine which method of entry is preferred by the local authorities.
Situation 2 – Power Failure with Battery Powered Convenience Open System
Many manufacturers of vehicular gate operators now offer battery powered convenience open systems that provide a method to open the gate when primary (AC) power is removed. DKS offers this type system in many of its gate operator products. This type of system is completely self-contained in the operator and is completely independent from the primary drive system. In essence, this provides a redundant drive system when the primary AC power is removed. Note: If your operator does not employ a battery back-up system, please refer to situation 3 below.
Operators equipped with a battery powered convenience open system typically operate in one of two different methods. 1) When a power failure occurs, the system immediately commands the gate to open and remain open, or 2) when a power failure occurs, the system remains in a stand-by mode until a command from either a wireless transmitter or manual switch is received to open the gate. In the second option, it is important to note that the radio receiver is powered from the batteries which allow the receiver to remain in operation during a power failure. This design feature assures that any emergency vehicle using the wireless transmitter method of entry will be capale of commanding the gate open even during power outages.
Battery powered convenience open systems in vehicular gate operators provide a trickle charge to the batteries during normal operation. It is advisable that maintenance personnel and property managers check these systems on a monthly basis to assure that the batteries are in good condition and have enough power to open the gate. Batteries in these systems are good, on average, for about two years before they will need to be replaced.
Situation 3 – Power Failure and Battery Powered System Failure
This is the “worst case” scenario that must be addressed during the design of the vehicular gate access system. In other words, system designers and installers must assume that at some point in time there will be a primary power failure and the battery powered convenience open system will fail to open the gate because of dead or low charged batteries or because of some other system component failure. Under these circumstances, the gate operator must assume a FAIL-SAFE mode. Simply stated, the operator “fails” in a safe condition allowing the gate to be manually pushed open without the need for any keys, cranks, or other mechanical devices. This is an essential feature for both emergency and non-emergency vehicles. Obviously, emergency vehicle personnel cannot waste time looking for keys, cranks, or attempting to force the gate open with bolt cutters, the “jaws of life” or other mechanical devices. They also cannot wait for maintenance personnel to arrive to activate gate release mechanisms that are typically located on the inside of the gate. Likewise, apartment and gated communities cannot allow a situation to develop where residents are “locked” out of their homes. Many Fire Department regulations require that “fail-safe” gate operators be installed to allow emergency vehicle access during power outages.
Automatic vehicular gate systems provide convenience and limit traffic in gated communities, apartment complexes, condominiums, and private homes and businesses. When vehicular access is restricted, there must be a means to allow emergency vehicles access in the overall design of the system. This design must include failure modes under the worst-case scenario, and the access system must have in place equipment and products to over come the worst-case situation. Automated Gate Services can provide you with vehicular gate products that meet these requirements.
Union Pacific Railroad
Union Pacific Railroad, one of America’s leading transportation companies teamed up with Automated Gate Services, Inc. to increase their perimeter security in Mira Loma, Ca. AGS supplied Fencing, Gates, Recessed Track, Automation, Safety Devices, Electrical and Turnstiles.
Results Per Page: